The SmartLink system, which has flow services enabled, identified a zone with flow usage that is lower than the user-defined low tolerance range.
What might happen as a result of the issue?
The identified zone will be skipped and the zone will try and run again during the next scheduled program.
The entire system will be shut down if it detects two zones in a row reporting flow usage outside of the user defined low tolerance range.
The problem may be the result of a clogged nozzle, clogged lateral line, a valve not fully opening, a crimped drip line, capped sprinkler heads or flow that is not reset.
Please sign in to leave a comment.